The Boston Fire Department along with Inspectional services and the Health Department has established a criteria of conditions for Exhaust Vent Cleaners and Inspectors who wish to perform work in the CITY OF BOSTON. These conditions are in keeping with the guidelines of the CITY OF BOSTON ordinance to “establish requirements for the cleaning of commercial cooking hoods and ventilation systems”.
Exhaust Vent Cleaners and Inspectors are required to pass an examination based on the most current NFPA 96 standard recognized by the Commonwealth of Mass.
This examination will be administered by a recognized organization http://www.ikeca.org/certification/us-regional-programs/boston-ma/exam-information that has proven to be of high standards, integrity and competence with regard to NFPA 96 regulations. The Boston Fire Department will list other recognized agencies that may administer the examination after careful review of their qualifications.
Individuals who have successfully passed the examination will also be required to submit documentation of five hundred (500) work hours experience in the cleaning and inspecting of exhaust vents. To waive this requirement the individual must have attended a recognized and approved training school.
Individuals who apply for an annual registration will be issued guidelines for reporting deficiencies found, posting of inspection stickers and other administrative requirements.
Advisory to all Exhaust Vent Cleaners and Inspectors
Be advised that all commercial hood and ventilation cleaning companies/contractors performing work in the city of Boston are required by law to issue deficiency reports to the establishment owner when they do not comply with NFPA 96 mandated repairs and also if there is no onsite exhaust system diagram. All deficiency reports must be given to the establishment and a copy forwarded to the Boston Fire Department - Fire Prevention Division by following the instructions listed on our website.
Commercial hood and ventilation cleaning companies/contractors must also report to the Boston Fire Department – Fire Prevention Division when an establishment in Boston does not renew their contract or if your company did not clean the hoods and ventilation systems by the scheduled date required in NFPA 96.
The Boston Fire Department’s Sample Cleaning and Inspection of Commercial Hood and Ventilation System & Deficiency Report has been updated, please revise your deficiency report to the form dated August 2010. All related information and required forms can be found below.
Think Safety First When Planning Your Barbecue This Summer
BFD offers tips and advice on barbecue safety.
A Few Quick Summer Safety Tips from BFD
Attached are a few quick summer safety tips from the Boston Fire Department...
New Requirements for Certain Lodging and Boarding Houses
On December 5, 2012 the Boston City Council adopted MGL Chapter 148 Section 26H requiring owners of lodging and boarding houses renting to 6 or more unrelated tenants to sprinkler their properties by December 5, 2017. (Click links below for more information.)
Restricted Use of Propane (LPG) for "Hot Work"
Effective January 1, 2013
Commercial Hood and Exhaust Cleaners
December 1, 2012 new guidelines from the Boston Fire Department that can affect commercial hood and exhaust cleaners registration
Sale or Transfer of Residential Dwellings
As of August 1, 2012, realtors and sellers scheduling Certificate of Compliance inspections should be aware that under MGL Chapter 148 sec 26F residential dwellings built after 1975 or having 6 or more dwelling units are exempt from the requirements of 26F.....
Candle Usage Guidelines, Definitions and Application for Candle Usage in a Place of Assembly
Read the new Candle Guidelines that are in effect October 1, 2012. The Boston Fire Department requires that the use of candles in a Place of Assembly be permitted as defined in the attached document.
New Crowd Manager Regulations
According to 527 CMR 10.13 effective June 1, 2011 a trained crowd manager must be present in any Nightclub, Bar, Discotheque, or Dance Hall with an occupant load of 100 or more persons during all hours when the facility is open to patrons.